go to site follow site giving babies viagra to kill a mockingbird racism essay levitra heath watch buy cialis at walmart go to site term paper layout description of a market scene essays can i get someone to write my essay global warming essay ppt follow site top essay editor sites for college source https://pharmacy.chsu.edu/pages/mla-research-paper-template/45/ pepene rosu viagra essay competition on azerbaijan to kill a mockingbird research paper topics levitra dooling source link a raisin in the sun essay questions nexium interaction with adderall nature vs nurture arguments for nurture essays writing a short essay write me an essay professional mba essay editor sites online tadalafil dapoxetine source condom with viagra gel viagra how long does it last with 100 mg go here Electrical Circuit for Off-Potential Measurement without SSD
Electrical Circuit for Off-Potential Measurement with SSD
What Happens while Measuring Off-Potentioal with SSD Connected
- When CP current (S1) is interrupted:
- The voltage across decoupler must change by the Icp x Rp voltage drop component that was eliminated
- A transient current must flow to make this voltage change
- Until this transient current is dissipated, an Off Potential measurement will not be measured accurately(too electronegative).
How to Measure Off-Potential with SSD
- OFF waveform analysis with a longer than normal On-Off cycle (e.g. 7 On, 3 Off)
- Determine the time after current interruption where a stable Off potential is reached
- Increase the measuring delay time according, if possible
- On some pipeline, increasing the measuring delay time will not be an option and this will be evident from the waveform analysis.
Dairyland Electrical Industries Technical Blog