get link cipro tabs and alcohol cheap viagra furthermore wellbutrin ordering online dissertation littéraire conclusion go site mill essay https://raseproject.org/treat/viagra-generic-in-uk/97/ presentation slides designs viagra beaverdale antithesis thesis synthesis go to site essay christmas with my family source can you use viagra if you don need it acheter viagra en ligne canada go site pay for essay writing https://blacklivesmatter.ca/chemist/l-arginine-better-than-viagra/18/ bunge essay mario realism scientific selected comic book speech bubble essay on euthanasia should be legalised go to link buy metformin without a script viagra and pericarditis see essay body paragraphs enter site idose viagra follow url fast will viagra work plan opinion essay cialis dunkirk Electrical Circuit for Off-Potential Measurement without SSD
Electrical Circuit for Off-Potential Measurement with SSD
What Happens while Measuring Off-Potentioal with SSD Connected
- When CP current (S1) is interrupted:
- The voltage across decoupler must change by the Icp x Rp voltage drop component that was eliminated
- A transient current must flow to make this voltage change
- Until this transient current is dissipated, an Off Potential measurement will not be measured accurately(too electronegative).
How to Measure Off-Potential with SSD
- OFF waveform analysis with a longer than normal On-Off cycle (e.g. 7 On, 3 Off)
- Determine the time after current interruption where a stable Off potential is reached
- Increase the measuring delay time according, if possible
- On some pipeline, increasing the measuring delay time will not be an option and this will be evident from the waveform analysis.
Dairyland Electrical Industries Technical Blog